We are common twin-screw air compressor is a common fault handling and maintenance, maintenance and routine maintenance in general, in addition to replacing the oil and filter there are other prone to other failures, the following we are analyzing.
1, the compressor can not start
First check whether the control voltage. If not, then check the fuse is intact; if there is a control voltage, then check the control relay and time relay operation is normal.
2, poor compressor start
Automatically shut down a few seconds after the boot from the electrical aspects of staff, such as whether the automatic air switch off, the voltage is normal, the intake valve is closed normally (the compressor can not be started with a load), and Y a start contactor and Three-phase motor is normal and so on.
3, the compressor does not supply gas
Check whether or control cylinder operation, if the operation check valve for mechanical failure; if no fault check whether there is load solenoid coil ISV suction; ISV exclusion of the solenoid valve coil and mechanical failure fault, then one investigation where the solenoid valve ISV Sub-circuit.
4, exhaust pressure is too low
First, check the pressure before and after the separation, the regulating solenoid valve and the manual valve 2SV like Leaks; endotracheal inspection and leak the road, whether the butterfly valve fully open, whether the intake regulator is operating normally, the solenoid valve 3SV, 8SV leaks, Pressure switch IPS need to readjustment and so on.
5, due to compressor oil injection and shutdown
First check the solenoid valve 5SV off the oil with or without voltage, the mechanical part is normal; if normal, check the check valve, reassemble or replace.
6, exhaust temperature is too high
Exhaust temperature is generally 80 ~ 95 â„ƒ. Failure to allow sufficient oil to cool will cause the temperature to rise too high to cause malfunction. First check the ambient temperature, compressor lubricants, oil level, oil, cooling fans, moving is normal; then check the oil cooler, the cooler is clean, the thermostatic valve element, cut solenoid valve voltage and the valve body portion Is normal, if the diaphragm is damaged, the temperature control spool does not move, you need to be replaced; finally check the oil filter is dirty or need to be replaced.
Evotec Special Generator including 6 Pole ,6 Pole Special Generator,6 Pole Generator,Three Phase 6 Pole Generator. Our alternator are widely used in industry, commercial, real estate, hospital, hotel, railway, telecommunications, data-centers and mining etc.
Speed: 1500rpm or 1800rpm
The specific technical features are listed below:
Frequency: 50 Hz or 60Hz
Number of Poles: 4
Power: up to 3500KVA
Voltage: 110V-690V,High Voltage:3.3KV-13.8KV
Insulation: class H
Power Factor: 0.8
Voltage Regulation Rate: Â±0.5%
Temperature Rise Class: class H
Ambient Temperature: 40
Overload:10% for 1 hour in every 12 hours
Degree of Protection: IP21 (IP23, IP44, IP54 on request)
- higher motor starting capability
- a reliable long life with superior class H insulation
- high thyristor load withstand capability for mobile phone and telecom applications
- ease of maintenance with integrated components and outboard exciter/rotating rectifier
- wide range of coupling discs/adaptor for single bearing configuration, suitable for wide range of engine brands
6 Pole Special Generator
6 Pole Special Generator
6 Pole,6 Pole Special Generator,6 Pole Generator,Three Phase 6 Pole Generator
EvoTec Power Generation Co., Ltd , http://www.evotecgen.com